Cross Connection Control Program
The Cross Connection Program is responsible for ensuring potable water provided by the City remains safe throughout the water distribution system and is protected from “backflow events.” (an undesirable reversal of potentially contaminated water from a customer to the City’s system.) This protection is achieved through the installation of backflow control devices and assemblies on the customers’ side of the meter. For most residential customers, backflow protection is provided by a dual check device in the meter box. For other services with higher risk, testable backflow assemblies are installed and required by Raleigh City Code to be tested by a Certified Tester. The results of the test are submitted to our web based system, Brycer-The Compliance EngineTM.
Failing to adequately prevent or control backflow events could have significant negative health and economic impacts, as evidenced by the Corpus Christi, TX incident in December 2016. http://www.cbsnews.com/news/corpus-christi-water-may-be-contaminated-texas-city/
Disconnection of Non-compliant Landscape Irrigation Meters Begins August 7, 2017
On August 7, the Public Utilities Department will begin disconnecting the irrigation meters of residential and commercial customers whose irrigation backflow assemblies have been non-compliant for more than 360 days. Non-compliant irrigation customers have been notified via email or by mail in 2016 and 2017, with many customers also receiving a phone call from our contractor. In June 2017, a final notice was hand delivered to non-compliant irrigation customers.
The disconnection process will be completed in phases throughout the months of August and September and coordinated so as not to impact normal meter reading schedules. Non-compliant customers will be given detailed information (see attachments) on how to bring their service into compliance once the disconnection process has started. Our Cross Connection and Customer Care and Billing Customer Service Representatives are prepared to answer calls and assist customers with questions. If you receive a call from a citizen concerning this matter, you may direct them to the Cross Connection Staff at 919-996-2747 or firstname.lastname@example.org.
Licensed Inspection Service Providers Required to Register with the City
The City of Raleigh's Office of the Fire Marshal and the Public Utilities Department Cross Connection Program have instituted a new process for service providers who inspect and test fire protection and containment backflow assemblies. Effective November 1, 2015 all compliant & non-compliant fire protection systems and containment backflow assembly test reports are required to be sent to The City of Raleigh electronically by your respective organization via The Compliance Engine's online system at www.thecomplianceengine.com.
The City of Raleigh is dedicated to delivering 100 percent compliance with our adopted Fire and Cross Connection Codes. This web based service will aggregate, track and streamline the collection of systems compliance data by providing the property owners with timely notification of their testing requirements, and affording the City the ability to better mitigate the risk in our community by improving public safety to our citizens.
All service providers licensed to inspect or test fire protection systems and/or backflow assemblies within the City of Raleigh are required to register and submit all test and inspection reports via The Compliance Engine per Raleigh City Code Article D-Water Quality Protection, Part 5 Chapter 2 Article B-Fire Prevention and Protection Ordinance. All reports must be submitted in accordance with the testing schedule and requirements outlined in Public Utilities Handbook Appendix A: Guidelines and Requirements for the Cross Connection Program.
Domestic/Fire Containment Assembly Testing Schedule:
Property owners who have containment assemblies installed on fire sprinkler systems as well as domestic services may test domestic containment assemblies in accordance with the annual testing date for fire containment assemblies. Property owners or certified testers are to contact the City of Raleigh's Cross Connection Program or contracted vendor to arrange this testing schedule exception. All other containment assemblies installed on domestic services are to be tested upon installation, replacement, and annually thereafter on or before annual test due date according to zip code:
|Zip Code||Annual Test Date||Zip||Annual Test Date|
|27529||September 1||27607||December 1|
|27545||May 1||27608||April 1|
|27560||December 1||27609||April 1|
|27571||January 1s||27610||September 1s|
|27587||January 1||27612||March 1|
|27591||May 1||27613||March 1|
|27597||May 1||27614||February 1|
|27601||October 1||27615||February 1|
|27603||November 1||27616||February 1|
|27604||August 1||27617||March 1|
|27605||October 1||27703||November 1|
Commercial & Residential Irrigation Testing Schedule
All residential irrigation containment assemblies are to be tested by July 1 every three years. Containment assemblies on commercial irrigation systems are to be tested annually by July 1. Testing of containment assemblies shall be conducted by a certified tester at the customer's expense. The owner shall cause such maintenance or repairs to be made, rendering the containment assembly fully operational. Additional testing and maintenance requirements may be requested or imposed as determined by the Raleigh Director of Public Utilities or his designee. It is the owner's responsibility to keep a complete, written record of any repairs and testing of the containment assembly for at least three years.
If you feel this notice was given in error, you may request an exemption to install an approved containment backflow assembly by submitting a Backflow Assessment Form
Owners of a facility containing a cross-connection that does not pose an imminent threat to the public water supply and who wish to apply for extension of time for compliance not to exceed one year from the date of the original notice issued pursuant to 8-2151 of the Raleigh City Code must proved the Cross Connection Coordinator in writing the following.
1. A completed City of Raleigh Extension Application
2. Three installations bids
3. Completion date for required work
4. Proof of existing or proposed containment assemblies for any severe hazards located within the facility by means a submittal of a passing operational test report
Check Your Irrigation System in Spring
When Spring arrives and freezing temperatures cease, many customers will begin to turn on irrigation systems and start watering again. Many water customers restart their irrigation systems by reinstalling the backflow assembly or hiring an irrigation contractor to perform this service for them. However, when you do so, you should take a few very important steps to make sure you do not damage pipes or irrigation components. Irrigation systems that are exposed to freezing temperatures can have busted valves and leaks. It is always best to hire a professional contractor to ensure your system is up and running with ease and efficiency. It is also an excellent opportunity to set the system controller for 'minimum' use. Healthy turf needs half the amount of irrigation most people use. Less frequent, but deep watering grows strong roots. Please reduce your use and use water responsibly. For more information or to verify backflow information you can email us or call 919-996-2742.
City of Raleigh: 919-996-2495
Wake County (Zebulon, Rolesville, Knightdale, Wendell): 919-856-6222
Town of Wake Forest: 919-435-9530
Town of Garner: 919-773-4433
Irrigation Testing Requirements
Information for testing your assembly
Instructions for terminating your irrigation service
Sec. 8-2149(b) All reduced pressure zone principle backflow prevention devices and double check valve backflow prevention devices shall be approved by the Foundation for Cross Connection Control and Hydraulic Research.
Our list is updated every 6 months. If you are a vendor and your backflow is USC and ASSE approved and not currently listed, please contact our Cross Connection office by email or call 919-996-2742.
Approved Assemblies List
List of assemblies allowed for 'new' and 'replacement' backflows in the Raleigh water area
Approved Test Equipment
The purchase of a bleeder valve kit and vertical tube kit is required for performing the Double Check Valve Assembly Test. These kits are available from the equipment manufacturer.
Test Kit Calibration Centers
Test kit calibration is required on an annual bases. Fax, mail, or email a copy of the calibration report to Cross.Connection@raleighnc.gov
Bavco Backflow Apparatus & Valve Co.
For Watts and Duke Test Kits
20435 South Suzanna Rd
Long Beach, CA 90810
Nicholson Lab Inc.
For Watts and Duke Test Kits
1423 Queen City Ave
Cincinnati, OH 45214
Specialty Valve & Controls Company
For Midwest Test Kits
3001 Griffith St
Charlotte, NC 28203
City of Raleigh Certification School
Certification Class: Agenda
Monday-Thursday 8 a.m. to 4 p.m.
Friday 8 a.m. to 12 p.m.
Recertification Class: Agenda
Wednesday 8 a.m. to 4 p.m.
Thursday 8 a.m. to 12 p.m.
For more backflow schools hosted by the City of Raleigh, please contact NCRWA.
NCRWA Certification Schools
|November 27-December 1||Open|
NCRWA Recertification Schools
NCRWA Cross Connection ORC School
NCRWA Backflow Repair School
- A completed registration form must be submitted for each student. Confirmation of enrollment to the course will be sent once the registration form and payment is received and all required documents have been submitted.
- Classes that have 8 or fewer students enrolled will be rescheduled. Classes will not exceed 15 students.
- Students who do not show up for class will forfeit the registration fee and will not be rescheduled for a future class.
- An alternate person may be sent in place of a student who cannot attend.
- Cancellations must be made in writing by mail or email within 5 days of the course to:
City of Raleigh
Public Utilities Department
PO Box 590
Attn: Linda Tillmon
Raleigh, NC 27602
Or email request to: Linda.Tillmon@raleighnc.gov
Please note that all refunds will be issued minus a $25.00 cancellation fee.
Orientation / Certified Testers
Not registered as a City of Raleigh Certified Tester?
If you wish to test in our water service area, you must be certified by one of our approved schools and attend one of the seven orientation sessions that will be conducted in 2015. Acceptance of your test reports cannot be made until you have successfully attended an orientation session and completed all paperwork to verify your certification.
Currently registered as a City of Raleigh Certified Tester?
In order to continue testing in our water service area, you are responsible to keep our records current with any renewals of your backflow certification and test kit calibrations. Test reports will not be accepted when submitted by testers with expired certificates.
Time: 8:30-11 a.m.
*The cost of orientation registration is included in the cost of the City of Raleigh's Cross Connection Certification and Recertification classes.
The City of Raleigh will accept certifications from the following schools:
City of Durham Department of Water Management
101 City Hall Plaza
Durham, NC 27701
919-560-4194 Ext. 35249
Durham's Backflow Prevention Program
Charlotte-Mecklenburg Utilities Department
5100 Brookshire Blvd.
Charlotte, NC 28216
704-399-2426 Ext. 295
Central Piedmont Community College Construction Education
Greenville Utilities Commission Water Resources Department
PO Box 1847
Greenville, NC 27835
North Carolina Rural Water Association
P.O. Box 540
Welcome, NC 27374
NCRWA Backflow Cross Connection Training
University of Florida Center for Training Research/Education for Environmental Occupations (TREEO)
3900 SW 63rd Blvd.
Gainsville, FL 32608